HEI0006464 - Sample Service History
23 /08/2020 – PGUK PDI – PAUL DAVIES
30/08/2020 – Into Service
29/10/2020 – 106 hours – Breakdown – RTP901. Failed AVR – Replacement parts dispatched from Mecc Alte direct to site within 24 hours. 30/10/2020 Steve Paskins (sunbelt) advised unit is running
11/11/2020 440 hours – Breakdown – RTP760. Shutting down on start up. Engineer attended site at Southampton Covid site same day. Engineer found the installation to be incorrect. Start / stop cables running behind busbar door blocking cut off switch. Cables run correctly. Generator left in working order.